Network communications are through the CsCAN protocol. Device programming is accomplished using a separate Personal Computer attached to the CCU300’s RS-232 Programming Port or through the CAN port.
Protocols Supported - CsCAN
Network Baud Rate - 125 Kbaud
Inputs Eight - (8)
Outputs Eight - (8)
Open Collector Outputs, Active LOW. Sink is 500 mA maximum, current limited, and suitable for driving inductive
A Cable Segment connects two nodes together. Each Cable Segment’s shield drain wire should be connected to the node’s SHIELD terminal at one end only. A NETWORK SEGMENT may be up to 1500 feet long, and connects up to 64 nodes together (using 63 Cable Segments). The RETURN terminal should be connected to the SHIELD terminal, on one node only, in each Network Segment. Up to 4 Network Segments may be connected together on a CsCAN network (using 3 CAN repeaters) with a total maximum of 253 nodes.