AS3760:2003 Safety inspection and testing of low voltage single phase and poly-phase (e.g. nominal 240v and 415v) electrical equipment connected to the electrical supply by a flexible cord.
The occupational health and safety OH&S act throughout Australia demands that portable electrical equipment including electrical hand tools such as saws and drills, as well as power boards, computers, power supplies, extension leads, kitchen portable appliances and all other electrical equipment that is used in the commercial and industrial workplace must be tested and tagged
Regular Checking of Electrical Equipment
The Victorian Energy Safety Regulator, Energy Safe Victoria (ESV), has received a number of incident reports from construction sites and other locations around Victoria where workers have suffered an electrical shock or burn while using faulty electrical tools and equipment that had a current test tag attached.
Equipment with a current test tag is not guaranteed to be safe for the remainder of the test cycle. ESV has seen many instances where the supply cord has been nicked, or the casing broken. exposing live parts to possible contact and electric shock on equipment with a current test tag fitted.
The following safety precautions should be adopted to prevent possible electrocution.
Test and tag electrical leads, tools and equipment regularly.
Visually inspect electrical leads, tools and equipment for damage before each use.
Use safety switches (also called RCDs) when using electrical tools & equipment.
Use competent people to repair damaged electrical leads tools and equipment
Use damaged electrical leads, tools and equipment.
Use electrical leads. tools and equipment in damp or wet conditions unless they are specially designed for use in those conditions.
Place electrical leads in areas where they may be damaged (e.g. on the ground, through doorways and over sharp edges).
Overload electrical circuits.
Use modified electrical tools and equipment.
Testing of Electrical Equipment
Portable electrical equipment including flexible electrical cords needs to be regularly inspected for wear and mechanical damage and periodically tested for earth continuity and insulation resistance.
Procedures for testing of electrical leads, tools and equipment and the frequency of these tests can be found in:
Joint Australian and New Zealand Standard AS/NZS 3760 In-service safety inspection and testing of electrical equipment; and
Joint Australian and New Zealand Standard AS/NZS 3012 Electrical installations - construction and demolition sites
ARK Testing | Electrical Testing and Tagging
ARK Testing Pty Ltd services melbourne and surrounds, we provide a complete testing and tagging service, that could include Three Phase Testing, Microwave Oven Radiation Testing, Thermal Imaging, Re-lamping Service, Appliance Repairs, Safety Switch(RCD) Testing, Exit and Emergency Light Maintenance.
We can test and tag your entire plug in electrical appliances from personal computers, to power tools, to 3 phase machinery.
Some examples of appliances that require testing are mobile phone chargers,fork lift chargers,kettles,televisions,power boards,welders,fridges,ovens,printers,monitors,
note book chargers,plug in radios,extension leads,electric power tools,lamps,microwaves,battery chargers,vacuum cleaners,photocopier,portable A/C and more
At ARK Testing we only use the top of the line, up-to-date testing equipment, the DeltaPAT with label printer and tablet to enter accurate appliance details. Our testing equipment allows us to safety test I.T. and Laboratory equipment without risk of damage.
Our staff are trained professionals, they are experienced in testing and tagging and know exactly what is required to ensure our customers gain compliance and are satisfied with the quality of our work.
Once our staff have completed testing and tagging, you will be supplied with a complete listing of items tested in Adobe pdf format. This register will include all information as required by AS/NZS 3760.