Ausafe Test and Tag conducts a 6 monthly and yearly procedure to ensure that the Australian Standard is being met.
Our emergency and exit light testing involves:
Ensure there have been no power interruptions for 16hrs prior
Inspection of fluoro lights for blackened ends, if observed replacement of tube is required
Testing of manual discharge for 90 minutes to simulated power failure. Light must stay illuminated for no less then 90 minutes
Reinstate light to normal operating condition and check that the battery charger operation indicator functions correctly
For Automatic discharge test. Ensure the unit operates correctly by a visual test to identify each indicator light is operational
Failed lights shall need replacement or repair
12 monthly testing is as above plus:
Cleaning of all light emitting and reflecting surfaces
Record all test results for both 6 month and 12 month testing and deliver to staff and place a copy in the switchboard
Ausafe Test & Tag | Electrical Testing & Tagging
Ausafe Test and Tag provide a range of services to assist in your obligation to comply with the OH&S legislation in your State or Territory.
The Occupational Health and Safety Act 1989 places a duty ...