Emergency and Exit Light Testing & Inspection Requirements Australian/New Zealand Standard AS/NZS 2293:1995.
Emergency escape lighting and exit signs for buildings
Part 2: Inspection and maintenance
The Standard sets out the periodic inspection and maintenance procedures which are necessary to ensure that emergency evacuation lighting systems will be in a state of readiness for operation at all times.
The Standard instructs that all Emergency evacuation lighting systems shall be inspected and maintained in accordance with the relevant procedures specified in the Standard and that the inspection and maintenance procedures shal be caried out only by persons having qualifications and experience suitable for this type of work.
All maintenance records must be in the form of hard copy record tags or log books. Electronic copies may also be used.
Six Monthly Procedures
Visual checks of all emergency and exit lights in mains operation.
Check for operation of maintained exit lights and replace faulty lamps where required.
Where manual discharge test facility is present, operate the test switch and/or circuit breaker to simulate a power failure.
The emergency lighting system shall remain illuminated for not less than 90 minutes.
Restore the emergency and exit lights to normal charging condition.
Check operation of all maintained exit lights and all charge indicators.
Report any failures and record data in on site manuals.
Record data in electronic format for auditing processes.
Twelve Monthly Procedures
Carry out all checks as per six-monthly procedures.
Clean all emergency and exit lighting diffusers as required.
Visual checks to ensure that the emergency lighting system operates in correct relationship to the normal lighting in any designated area.
Perth Testing and Tagging was established in 1994 to help Australian businesses meet their electrical safety obligations.
As their business developed, it became evident that businesses were not adhering to Australian Safety Standards AS/NZS 3760:2010.
After lengthy research they identified that most companies wanted to meet their OHS reasonabilities but did not have the expertise or the manpower to do this. This is where Perth Testing and Tagging can help: they have established a specialised business within Australia devoted to electrical safety testing.
Their services include:
• Electrical Testing and Tagging
• Emergency Light Testing
• RCD Testing
• Thermal Imaging
• Microwave Leakage Testing
Their head office is located in Perth, WA. However, as their client base has grown they have developed a nationwide service with testing teams in every state, providing excellent customer service.
Their business continues to grow and so does their expertise, enabling them to offer their services to any business.